Quad T260 Alternating Alarm Panel
The Quad T260 Alternating Alarm Panel is custom designed for use with E/One quadplex grinder pump stations.
Quadplex Grinder Pump installations, a station with four grinder pumps , require that the pumping load is shared equally among the four pumps. Under normal conditions two pumps remove the accumulated sewage from the grinder pump basin.
After 24 hours, the Quad T260 Alternating Alarm Panel toggles the electrical supply power to the pumps that were idle. If the sewage level reaches the alarm level, the four grinder pumps will operate simultaneously for 3 to 4 minutes. If after that time the sewage is not below the alarm level, the alarm circuit is engaged.
The Quad T260 Alternating Alarm Panel is supplied with audible & visual high water level alarms. The panel is easily installed in accordance with relevant national and local codes. The Quad T260 Alternating Alarm Panel is listed by Underwriters Laboratories to ensure high quality and safety.
• Corrosion-proof polymeric enclosure
• NEMA 4X rated enclosure
• Lockable latch with padlock
• Circuit breakers
• Terminal blocks & ground lugs
• Dry Contacts
• Lead/Lag indicator lights
• Alarm indicator lights
• Run indicator lights
• Manual push-to-run
• Generator receptacle with auto transfer
Drawings & Manuals
Quad T260 Alternating Panel Drawings (PDF)
Quad T260 Alternating Panel Drawings (zipped DXF)
Quad T260 Alternating Panel Specification (DOC)